- 1 What is the difference between NM cable and NMC cable?
- 2 What does type NM-B mean?
- 3 What does the B stand for in NMB cable?
- 4 What is the difference between U B B and NM-b wire?
- 5 Is Romex NM-B?
- 6 Can nm-B be exposed?
- 7 Can type NM-B Romex be exposed to corrosive vapors?
- 8 Is Romex suitable for outdoor use?
- 9 What type of wire should be used outdoors?
- 10 Where do you use BX wire?
- 11 What is Romex called in the code book?
- 12 At what intervals does nm need to be secured?
- 13 Is BX cable better than Romex?
- 14 What is NM BX or conduit?
- 15 What does BX wire stand for?
- 16 Is BX wiring safe?
- 17 Can you connect Romex to BX?
- 18 Can BX cable be used as ground?
What is the difference between NM cable and NMC cable?
The only difference between the two definitions is that NMC is corrosion-resistant and NM cable is not. NM cable can only be installed in dry locations, while NMC can be installed in dry, moist, damp and corrosive locations.
What does type NM-B mean?
Non-Metallic Sheathed Cable
Type NM-B (Non-Metallic Sheathed Cable) is commonly used for residential wiring of luminaries, devices and appliances. Type NM-B ampacity limitation shall be in accordance with the 60ºC conductor temperature rating, as specified in the NEC.
What does the B stand for in NMB cable?
NMB stands for non-metallic because it has a PVC jacket instead of a metal-clad jacket. It is a basic indoor electrical wire used to deliver power from an electrical box to lights, outlets and appliances.
What is the difference between U B B and NM-b wire?
The primary difference between standard NM and underground feeder (UF) cable is in the cable construction. Standard NM cable contains wires that are wrapped with paper and a relatively loose plastic sheath. UF cable has wires that are completely encased in solid plastic.
Is Romex NM-B?
Southwire® Romex® Brand SIMpull® NM-B (nonmetallic-sheathed) cable may be used for both exposed and concealed work in normally dry locations at temperatures not to exceed 90°C (with ampacity limited to that for 60°C conductors) as specified in the National Electrical Code.
Can nm-B be exposed?
NM cable, also known by the trade name Romex, is the most common form of electrical wire used in residential electrical work. … The sheathing on both 14 and 12 AWG wire is 15 mils thick. Still, no matter how strong the NM sheathing, it is not meant for exposed applications.
Can type NM-B Romex be exposed to corrosive vapors?
Section 334.12(B) does not allow type NM cable to be installed in wet locations or where exposed to corrosives such as chlorine but without the revised code language, sections 334.10 and 334.12(B) were in conflict with one another.
Is Romex suitable for outdoor use?
Romex© Outdoor Conduit. Romex is a type of electrical wire used in various applications. … Romex wires cannot be used outdoors because, if it gets wet with water, gas, oil or another solvent, these liquids could penetrate the jacket and ruin the connection by getting in contact with the bare copper ground wire.
What type of wire should be used outdoors?
Exposed or buried wiring must be listed for its application. (Type UF cable is the most commonly used nonmetallic cable for residential outdoor wiring runs.) UF cable can be direct buried (without conduit) with a minimum of 24 inches of cover.
Where do you use BX wire?
Electrical cable encased in metal sheathing is often used in basements and other areas where the wire is not encased in a finished wall. It is handled differently than standard Romex® (non-metallic sheathed) cable. It is often used in fire-rated occupancies as an alternative to metallic conduit.
What is Romex called in the code book?
Romex™ is a common type of residential wiring that is categorized by the National Electrical Code (NEC) as underground feeder (UF) or non-metallic sheathed cable (NM and NMC).
At what intervals does nm need to be secured?
NM cable must be supported and secured every 4 ½ ft. and within 12 inches of every outlet box, junction box, cabinet, or fitting.
Is BX cable better than Romex?
BX cables are safer and protect against any accidental penetrations. Romex cables have vinyl sheathing that you can penetrate easily. A BX cable usually is grounded through an internal plastic-coated ground wire or metal armor.
What is NM BX or conduit?
BX is also known as Armor Clad or Flexible Metal Conduit cable. BX is sheathed in a flexible metal spiral made either from aluminum or galvanized steel. BX provides all the advantages of NM cable plus some additional benefits. The flexible metal sheathing is easy to install, about as easy as NM cable.
What does BX wire stand for?
Armored cable (AC) first appears in the 1903 NEC. There were originally two initial versions of armored cable. One was called “AX” and the other “BX,” with the “X” standing for “experimental.” The “BX” version became the one that eventually was produced, and hence the name “BX” became the common name.
Is BX wiring safe?
The actual name for it is “Armored Cable” or AC, but many people call it by its original trade name “Greenfield” or just BX. Modern BX wiring, properly installed, is safe. It is acceptable to the latest version of the National Electrical Code (2017 NEC Article 320).
Can you connect Romex to BX?
Can BX cable be used as ground?
A chief distinction between BX and NM is that BX can achieve grounding through the outer metal casing. This casing needs to be attached to metal boxes. Another distinction is that some types of BX cable can be installed in exposed locations, either indoors or outdoors.